Just some food for thought.
Originally posted on Onward and Upward:
Responding to recent comments from a facility manager that fires in data centers are rare, Onward and Upward offers a recap of three such fires that have happened in the previous 11 months with details on each.
♦ A fully-powered, but unused transient-voltage surge suppressor (TVSS) failed in the Hoover State Office Building’s basement level data center on the afternoon of February 18, 2014. The failure caused significant damage to the unit and produced smoke throughout the room. A quick-thinking employee activated a manual release station that discharged over 2,400 pounds of FM-200 clean fire-suppressing agent throughout the room and raised floor. In addition, the agent release also triggered the emergency-power-off circuit dropping power to critical equipment.
The Des Moines, Iowa fire department responded within minutes of receiving the signal from the building’s automatic fire alarm system. Upon arrival, the fire was extinguished and personnel were assessing the fire…
View original 304 more words